Today’s routine generator test passed as expected.
The test was run on-load to verify fitness for a planned maintenance window on the mains supply next week.
The generator was started automatically after detecting the mains isolation, then ran on-load 10:17 – 10:40
The generator detected recovery of mains and shut down automatically in the expected timeframe
All measured values were within their normal ranges.